The KYN-24 AC Metal-Enclosed Switchgear And Controlgear (hereinafter referred to as switchgear)manufactured by XJ is a complete set of distribution apparatus designed for 24kV three-phase AC 50Hz single busbar and single busbar segmented system. It is mainly applied in power plants, power transmission from small and medium generators, power distribution in industrial and mining enterprises, and energizing and power transmission of secondary substations and startup of large HV motor in the electric power industry system, so as to realize control, protection and detection.
Such switchgear meets the requirements set out in IEC298 and GB3906-1991, and has the interlock function that can prevent from pushing and pulling a circuit breaker handcart with load, opening and closing a circuit breaker mistakenly, opening and closing a circuit breaker when the earthing switch is in closed position, entering the charged compartment accidentally and closing the earthing switch mistakenly with charge. It can be configured with our handcarts with various functions such as VEM-24 indoor high-voltage vacuum circuit breaker, isolation handcart, fuse handcart, PT handcart, metering handcart and transformer handcart. It can be designed to be multiple types and satisfy various design demand, and is really a distribution apparatus with superior performance.
For more details,pls contact us.
The following materials shall be provided when orders are placed:
1.Main wiring scheme No., and systematic single line diagram, arrangement diagram and layout;
2.The user shall provide the secondary function diagram and terminal arrangement diagram. If there is no terminal arrangement diagram, it shall be prepared by the manufacturer;
3.Summary of model, specifications and quantity of internal elements and electrical equipment in the switchgear;
4.The span and height shall be provided if busbar bridges are required (busbar bridge between two rows of cabinet and between wall and cabinet);
5. Use of switchgear in special service conditions shall be stated when the order is placed;
6.The type and quantity of other accessories needed or accessories beyond the accessory supply scope shall be provided.